From pv magazine USA
The North American Electric Reliability Corporation (NERC) has published research detailing multiple grid events that produced solar power outages across a region. One pattern that has arisen is that a grid asset abnormality occurs, like power plants tripping or fires causing shorts. Solar assets react by lowering output for a short to medium amounts of time, versus ‘riding through’ these events.
A West Texas event earned NERC analysis after a single-line-to-ground fault on a generator step-up transformer at a combined-cycle power plant led to a reduction of 1,178 MW of solar PV resources – up to 200 miles away. NERC later released Multiple Solar PV Disturbances in CAISO, which described why more than 100 utility-scale solar plants, and a significant amount of distributed solar, shed gigawatts of capacity during grid fault events in the spring and summer of 2021.
NERC has now released an analysis of the Blue Cut and Canyon 2 Fire disturbances in August 2016 and October 2017. The report is a product of ongoing work by the Inverter-Based Resource Performance Task Force.
The report notes that the Blue Cut Fire caused a 500 kV line fault and led to a temporary loss of 1,178 MW of solar. NERC said inverters were tripping erroneously on instantaneous frequency measurements, and that most of the units quickly ceased injecting energy into the system when voltage measurements fell outside of a standard range.
The Canyon 2 fire caused “phase-to-phase” faults on 220 kV and 500 kV transmission lines. These events caused the reduction of solar output “across a wide region of the Southern California Edison footprint.”
It was suggested that the main issue of the Blue Cut Fire (inverters tripping on calculated frequencies) was mitigated at Canyon 2. However, a list of additional challenges were noted:
- Inverters continued to use momentary cessation as a form of ride-through
- Plant-level controller ramp rates were interacting with the recovery from momentary cessation
- Many inverter protective controls were set solely based on the PRC-024-2 voltage curve, rather than actual equipment limitations
- Many inverter protective controls were set to trip for instantaneous voltage over 1.2 pu, using an unfiltered measurement
- One inverter manufacturer reported phase lock loop (PLL) synchronization issues
- One inverter manufacturer reported tripping on dc reverse current that required a manual reset at the inverter
NERC also suggested that “transient interactions between momentary cessation, transient overvoltage, and in-plant shunt compensation” will warrant further investigation. Prior reports have suggested that many inverter problems could be solved by correcting settings or performing basic updates.
This content is protected by copyright and may not be reused. If you want to cooperate with us and would like to reuse some of our content, please contact: firstname.lastname@example.org.
By submitting this form you agree to pv magazine using your data for the purposes of publishing your comment.
Your personal data will only be disclosed or otherwise transmitted to third parties for the purposes of spam filtering or if this is necessary for technical maintenance of the website. Any other transfer to third parties will not take place unless this is justified on the basis of applicable data protection regulations or if pv magazine is legally obliged to do so.
You may revoke this consent at any time with effect for the future, in which case your personal data will be deleted immediately. Otherwise, your data will be deleted if pv magazine has processed your request or the purpose of data storage is fulfilled.
Further information on data privacy can be found in our Data Protection Policy.