French floating PV specialist Ciel&Terre—known for its proprietary Hydrelio floating platforms—and Japanese electronics manufacturer Kyocera have announced that the 13.7 MW Yamakura floating PV plant in Japan is currently being reconstructed, 16 months after Typhoon Faxai destroyed a big portion of the facility.
“The Yamakura incident happened in September 2019, when one of the five strongest typhoons in 60 years (named Faxai) occurred in the Chiba area, with wind speed recorded at up to 207kmh,” Ciet&Terre said in a statement. “Due to the typhoon’s unusual strength, a part of the floating PV plant was impacted and needed to be rebuilt.”
“One floating island with a complex shape has been changed to smaller islands with a square shape, to avoid stress concentration,” a company spokesperson told pv magazine. “The design with square shapes increased safety factors.”
The company also recalled that the Japanese Ministry of Economy, Trade and Industry (METI) started an investigation after the incident and said that its experts and those of Kyocera TCL Solar cooperated with the ministry in a “highly professional manner, to leave no stone unturned, and make sure underlying causes of the incident were fully understood.”
The final, root causes identified by the METI investigation, which was concluded in April 2020, were the island size and shape, the stress concentration load, and the safety factors used during construction. “The Hydrelio structure engineered by Ciel & Terre is not in question,” the French company specified. “Client investigations have been additionally done on different parts of the Hydrelio structure to confirm there was no damage from degradation over time.”
In its report, METI had concluded that the main cause of the accident was anchor failure. The floating island was held in place by 420 anchors, which connected to a total of 823 mooring lines. During the storm, seven anchors came loose on the central, southern end. After the anchors failed, the resin bolts started to collapse because the wind loads were now dissipated more unevenly. After each collapsed bolt, the loads on the adjacent ones increased, causing a chain reaction. In this way, the array was ripped into three parts. The shape of the plant also played a role, according to the ministry.
The reconstructed portion of Yamakura floating PV plant has not resumed commercial operation yet. “We will provide an update in June,” Ciel&Terre's spokesperson said, without providing further details.
*The article was amended on February 25 to reflect that the reconstruction of the plant is not fully completed, as we previously reported.
This content is protected by copyright and may not be reused. If you want to cooperate with us and would like to reuse some of our content, please contact: email@example.com.
Good Reporting & Congrat
The article would have been made more impressive and interesting by providing the pictures of anchors prior and after failure of anchors and resin bolts. The failure of anchors were attributed to What (?) -uplift effect of water waves / wind passing underneath the panels and escaping at the ends or water waves+ wind passing underneath the panels and escaping at the ends
I suggest the above photographs will also be included in June forthcoming Report
By submitting this form you agree to pv magazine using your data for the purposes of publishing your comment.
Your personal data will only be disclosed or otherwise transmitted to third parties for the purposes of spam filtering or if this is necessary for technical maintenance of the website. Any other transfer to third parties will not take place unless this is justified on the basis of applicable data protection regulations or if pv magazine is legally obliged to do so.
You may revoke this consent at any time with effect for the future, in which case your personal data will be deleted immediately. Otherwise, your data will be deleted if pv magazine has processed your request or the purpose of data storage is fulfilled.
Further information on data privacy can be found in our Data Protection Policy.